Model 1047-LPDOME Locking Suspended Ceiling Tile Wi-Fi Access Point Enclosure
Economical, locking, 2 x 2 ft. suspended ceiling Wi-Tile enclosure mounts and secures Wi-Fi and Small Cell APs flush to the ceiling. This steel enclosure replaces a standard ceiling tile, and its larger back-box is suitable for larger APs and antennas. The interchangeable door simplifies AP and antenna moves, adds, and changes. APs are mounted in the door, or inside the models with the ABS plastic dome. Styles available for both standard flush grid and recessed grid ceilings (-T), and for both North American and European (metric) ceiling systems.Attractive, textured, powder-coat finish matches many ceilings
Larger back-box designed for securing most vendors' enterprise Wi-Fi and Small Cell APs
Interchangeable doors permit simple migration to new APs and antennas
Enclosure back-box is an effective dust barrier to simplify ICRA procedure compliance
Features & Benefits
Design: Economical ceiling tile enclosure designed for APs with integrated antennas. Fits into standard 2 x 2 ft. (U.S.) ceiling grid. Doors available for all leading AP vendors models (see Oberons Model 1047 configuration guide)
Performance: UL listed for low voltage applications, and designed to meet NEC300-22 and 300-23 for plenum installations. OSHPD approved, OPM-0110-13. De-rate AP operating temperature range by 6ฐC when mounted in enclosure
Locking, quick release interchangeable door for migration to other APs. Large door permits migration to large APs and domes
Firestop grommet for insertion into back-box, large enough for 2 Cat6A cables
1 in. trade size knockouts in four walls
Construction: 20 ga. galvanized steel back-box. 18 ga. white, powder-coated steel flange and door. Solid back-box fills opening behind AP, creating an effective fire, smoke and dust barrier to simplify ICRA compliance. Model 1047-LPDOME and 1047-DOME only: Paintable UL 94-5VA ABS plastic dome, dome is virtually transparent to wireless signals)
Constructed to be compliant with City of Chicago Environmental Air (CCEA) plenum requirements
Enclosure must be supported by the building structure, independent of the suspended ceiling, per NEC paragraph 300.11. Includes hanger wire
Maximum weight inside enclosure is 25 lbs.
For recessed grid ceilings, specify "T" for tegular flange units
Size: 23.75 x 23.75 x 3 in. (603 x 603 x 76 mm). Back-box is 18.5 x 18.5 x 3 in. (-LPDOME total depth is 5 in.)
Specify "-600MM" for European (metric) ceiling (594 x 594 mm tile flange. All other dimensions are the same)
Standards for Safety
UL 2416, Audio/Video, Information and Communication Technology Equipment Cabinet, Enclosure & Rack Systems
CSA C22.2 NO. 60950-1-07 + Amd. 1 Amd. 2 Information Technology Equipment -- Safety. Part 1, General Requirements
OSHPD Approval OPM-0110-13
Measurements (Maximum values):
Width: 23.75 in.
Height: 23.75 in.
Depth: 3 in.
Item Weight: 16 lbs
Shipping Weight: 20 lbs.
Enclosure and door
(1) Dual Cable Egress Firestop Kit (1 in. trade size conduit connector and firestop grommet)
(2) Keys for lock
(4) Hanger wires